It is the Controller to operate distribution automation equipment composed of four circuit breakers or switches on sites. It is mainly used as a control panel for local control and it indicates equipment status such as RMU. Also, it can provide equipment status to RTU through contact point, and it has a pass-through function that can operate Switches or breakers by receiving control output from the RTU.
Input Power: AC 110/220V, or user standards
Monitoring contact status for four circuits and status indication(Open, Closed, or Earthed)
Safety button(Open, Close) to operate breakers or switches of each circuit
Monitor a storage battery charging part, a storage battery, and power status as well as a battery test button
Select a storage battery separation time and indicate it
Indicate operation mode (Local/Remote) and selecting switch
Provide various information to the RTU, etc. by dry contact
Onsite operations for the equipment that includes RMU or multi-circuit such as underground switch
System establishment for the purpose of integration with automation systems in the future
By using together with the Relay to build a system to prevent faults on customers from spreading to trunk lines
It primarily aims of field-centered equipment operation, but it can be extended by additional devices such Relay.
Automatic operation is possible through the interface with separate RTU
It is possible to expand systems by stages, so it can share total input cost. It is possible to design a system in accordance with environments.