The SF6 gas insulated sectionalizer is equipped with an electrically operated, spring- charged operating mechanism. The closing operations are performed after the spring for opening operation is fully charged, and a spring-charged operating mechanism is applied to perform fast and accurate opening operations with little energy.
The sectionalizer is equipped with voltage sensors in each bushing on both sides, and current sensors in each bushing on the source side to measure electrical quantities of distribution lines.
In order to guarantee constant opening and closing speed and operation reliability, a sufficiently field proven mechanism is adopted.
The tulip-shaped contacts made of material with excellent electrical properties guarantees stable mechanical and electrical operation performance.
|Applicable Standard||IEC 60265-1, ANSI C37.71|
|Rated Voltage (kV)||25.8 kV|
|Rated Current (A)||400A|
|Rated Frequency (Hz)||60Hz|
|Rated Short-Time Current (kA)||12.5kA, 1sec|
|Rated Making Current (kAp)||32.5 kA|
|Rated Power Frequency withstand Voltage (kV)||60kV|
|Impulse withstand Voltage (kV)||150kV|
|Operating Mechanism||Manually Operated and/or Motorized|
|Bushing Material||Porcelain / Silicone|
Used as a sectionalizer to prevent faults near the end of lines or on the customer side from spreading to the entire system in conjucnction with the reclosers.
Used as a switch for load shedding to maintain power quality of distribution lines.
Used as a switch to sectionalize some sections in branch lines or customer service lines.
Auto section switch control for KEPCO.
BR-10A sectionalizer control.
SC-100NC sectionalizer control without communication capability.
BH SYSTEM249-14, Soltaesangdu-gil, Hyangnam-eup, Hwaseong-si, Gyeonggi-do, KOREA
COPYRIGHT (C) BH SYSTEM. ALL RIGHTS RESERVED.Designed by Molto.